Microinverter Hoymiles HMS-1600-4T 1600 VA 4 MPPT

2025-04-16T12:25:02+02:00

Vendor: Tepto
Type: Inverter
Price: 231.00

Hoymiles HMS-1600-4T Microinverter

The Hoymiles HMS-1600-4T is a high-performance microinverter for photovoltaic systems with up to four solar modules. With an output power of 1600 VA and four independent MPPT inputs, it ensures optimal energy yield and high operational reliability.

Thanks to modern communication technology and high efficiency, the inverter is suitable for both private PV systems and commercial applications.

Highlights & Advantages

⭐ 1600 VA output power for high-performance PV systems

⭐ 4 independent MPPTs for maximum energy yield per module

⭐ High efficiency up to 96.7% for efficient operation

⭐ IP67 protection rating for reliable outdoor use

⭐ 4-in-1 design for reduced installation costs

Area of ​​application & Target audience

The Hoymiles HMS-1600-4T is suitable for:

Private customers with rooftop photovoltaic systems

Plumbing, heating and electrical contractors

New construction and renovation projects

Small to medium-sized PV systems in single-family homes

Everyday benefits

Thanks to module-by-module power optimization, each PV unit operates independently. Shading or different orientations of individual modules therefore do not affect the overall performance of the system.

The integrated monitoring enables transparent system control via the S-Miles Cloud. At the same time, the fanless cooling reduces maintenance requirements and increases service life.

Technology & equipment

The microinverter features four separate MPPT trackers and can directly connect up to four solar panels. Communication is via a stable sub-1G wireless solution.

Installation is carried out via AC trunk cabling systems, enabling flexible and scalable system integration.{index=0}.

4 MPPTs, each with one input

Galvanically isolated RF transformer

Natural convection (no fans)

Integrated grid protection according to VDE-AR-N 4105

Efficiency & Environment

With a CEC peak efficiency of up to 96.7%, the HMS-1600-4T operates particularly efficiently and reduces energy losses to a minimum.

Compliance with relevant standards such as EN 50549-1 and VDE-AR-N 4105 ensures safe and grid-compliant operation.

compatibility & System integration

The microinverter is designed for standard PV modules in the power range of approximately 320 to 540+ W.

It can be flexibly integrated into existing and new PV systems and is compatible with Hoymiles DTU gateways for monitoring.

Technical data

Manufacturer | Hoymiles Power Electronics Inc.
Model | HMS-1600-4T
Product type | PV microinverters
Nominal output power | 1600 VA
Max. input voltage | 65 V
MPPT voltage range | 16 – 60 V
Number of MPPT | 4
Max. input current | 4 × 14 A
Max.Short-circuit current | 4 × 25 A
Nominal voltage | 220/230/240 V
frequency | 50/60 Hz
efficiency (CEC) | 96.7%
Protection class | IP67
Dimensions | 331 × 218 × 36.6 mm
Weight | 4.7 kg
cooling | Natural convection
Ambient temperature | -40 to +65 °C
communication | Sub-1G
Standards | EN 50549-1, VDE-AR-N 4105

Scope of delivery

1x HMS Inverter 1600

Assembly & User manual

Accesories & System recommendation

The operation of the Hoymiles HMS-1600-4T requires additional system components such as AC trunk cables, DTU gateway and mounting material.

Suitable system components

Photovoltaic accessories

inverter

Photovoltaic systems

Hoymiles DTU Gateway

Assembly and safety instructions

Installation must be carried out exclusively by qualified personnel. The inverter must be mounted below the PV modules and protected from direct weather exposure. A minimum distance for ventilation must be maintained.

FAQ

How many modules can be connected?

Up to four PV modules can be connected directly to the microinverter.

Is the inverter suitable for outdoor use?

Yes, thanks to IP67 protection, outdoor use is easily possible.

Do I need a monitoring system?

For monitoring, a Hoymiles DTU gateway in combination with the S-Miles Cloud is recommended.

Which standards does the device meet?

The inverter complies with, among others, EN 50549-1 and VDE-AR-N 4105.

Is network protection integrated?

Yes, integrated network and plant protection is present and certified :contentReference[oaicite:5]{index=5}.

Which module power output is suitable?

Typically, PV modules in the range of 320 to 540 W are suitable.